A series of non-metallic connectors designed to provide a liquidtight seal when terminating liquidtight non-metallic conduit (U.L. Type B) or liquidtight non-metallic tubing to a box or enclosure with knockout opening or a threaded hub.
T&B Bullet meets performance requirements when terminating Type B liquidtight non-metallic conduit or flexible non-metallic tubing to a box or enclosure with knockout opening or threaded hub. Outside surface has friction reducing ridges. Inner surface teeth bite into conduit or tubing to enhance clamping and sealing action. Fitting ferrule designed to accept variations in conduit sizes and field conduit cuts. Smooth ferrule profile reduces friction to ensure a tight conduit-to-fitting seal.
Thomas&Betts 1/2in 90° Liquidtight Flexible Non-Metallic Conduit Fitting Characteristics: • Trade size: 1/2 inches• Material: thermoplastic • Dimension A (inches) 0.570, A (mm) 14.48 • Dimension B (inches) 1.489, B (mm) 37.82 • Dimension C (inches) 1.448, C (mm) 36.78 • Dimension D-Minimum Throat (inches) 0.55, D (mm) 13.97 • Dimension F (inches) 1.986, F Approx. (mm) 50.44 • RoHS Compliant • A±0.015 (0.040) in. (mm): 0.570 (14.48) • B±0.035 (0.90) in. (mm): 1.489 (37.82) [after assembly] • C±0.015 (0.40) Across corner in. (mm): 1.448 (36.78) • Min. throat dia. D in. (mm): 0.550 (13.97) • E thread NPT: 1/2-14 •F (in.) (mm) approx.: 1.986 (50.44) • Body Gland-Weather stabilized thermoplastic (black) • “O” Ring - Nitrile (blue) • Locknut - Steel/ electro zinc plated • Matl. temp. rating - Thermoplastic - 40°C to 105°C • Material Flammability Rating: UL94-V2 • 2-year warranty
Conforms to: • Suitable for hazardous locations; Class I Div 2; Class II Div 1 & 2; Groups E, F, G; Class III per N.E.C.; Article 501-4, 502-4 and 503-3 • C.S.A. 22.2 No. 227.2 & C.S.A. 22.2 No. 227.3 • ANSI/UL514B-1988 • Watertight requirements of NEMA Type 4 and NEMA Type 6 enclosures • Federal Standards H28 (NPT threads)
Listed/certified by: • U.L (File No. E23018) • C.S.A. (File No. LR52391) • (ISO threaded fittings not included)
Where liquidtight flexible nonmetallic conduit (UL and CSA Type B) or liquidtight flexible nonmetallic tubing is terminated to a box or enclosure, the nonmetallic fittings used shall be able to be installed without disassembly and provide a positive installation criteria. In the installed condition, the fitting must provide a seal meeting watertight requirements of NEMA Type 4 and Type 4X. The performance of fittings shall be unaffected by exposure to detergents, sanitizers, cutting fluids, wire pulling compounds and oil-based industrial paints. The fitting must also be capable of withstanding marine environment and cold impact simulating a hammer blow. Installed fittings shall be of the elongated gland type as manufactured by Thomas & Betts LT38P Series.